With summer hereabouts, we all recall about hot days ahead and all the fun activities that go by with the season; but summer heat is not something we look onward to for our computers.To guard computers, data centers should be well covered with no windows to the outside to manage summer heat away from delicate equipment.
Cooling is a large percent of the running cost of running your data centers and to extra save on costs of cooling, this is a list of fundamental best workouts that can help maximize the cooling systems in your raised floor environment and help lower your running costs. Data Center Cooling
-Constantly use hot/cold aisle arrangement, when possible, to maximize cooling from your systems. By not using this arrangement, you will blow hot exhaust air from one row of servers into the next server row's intake vents. Data Center Airflow management
-Cold Aisles should constantly be two tiles wide. Only place penetrated tiles in these aisles.
- Install brush grommets to maintain the static pressure maximized under the raised floor and gain maximum delivery of cold air to your cold aisles. By not using brushed grommets, you waste cool air in areas not wanting cooling which increases your running costs and makes your cooling system less effective.
-When connecting and removing power whips or communication cables, eliminate no more than six raised floor tiles at a time. Eliminating more than six tiles can cause a meaningful drop in static pressure under the raised floor and make equipment to overheat.
- Blank off unused server rack locations. Unblocked open racks can cause bypass air from the hot aisles to mix with cold aisle tempering the input air to your servers. Data Center Airflow efficiency
Success in a data center can be estimated in up time, the more the better. Every data center facility manager's goal is to get the best up time, and that cannot be achieved if critical electrical elements sensitive to temperature are allowed to overheat. The solution to controlling heat in a data center is proper airflow management. Building and maintaining basic airflow management practices will enhance your chances of continuous up time. Data Center Airflow